180 glasses per hour (based on 167 ml glass)
BREEAM compliant when fitted with optional BREEAM kit.
Kit comprises stainless steel side panels and top panel as illustrated.
Ensures chiller securely fixed to the wall and protects against vandalism.
Chiller has adjustable foot and can be bolted to the floor.
Chiller must be positioned 60 – 70mm from the wall to allow adequate ventilation.
Chilling requires the ambient temperature to be between 10°C and 45°C.
Must be installed by a suitably qualified person.
Supplied with all fittings required including adaptors to facilitate connection to 15mm copper pipe.
Minimum water pressure 1 bar.
Maximum water pressure 3 bar, if higher than this a pressure reducing valve is required.
Installation must comply with current IEE regulations.
The product should be connected to the fixed wiring of the property via a double pole fused spur with a minimum break capacity of 13 amps.
Cable pre-wired (1.5m), entry to the back of the unit.
Sanitise every 3 to 6 months.
Replace filter approximately every 6 months.
See product instructions for full maintenance requirements.
1 year parts or replacement warranty.